Prices are tax included
Make sure the Thermostat is within 1m of Fibaro Home Center and put Fibaro Home Center into Inclusion mode.
Put the Thermostat into Learning Mode: In the SCS317's menu this is Setup > Set up Z-Wave > Learn'. Press the Thermostat's ENTER' button twice. Scroll through the menu by pressing the + arrow button until Setup appears in the display. Press ENTER. Scroll to Set Up Z-Wave and press ENTER. Scroll to Learn and ENTER.
Now you should see message (Waiting for network data).
Choose Devices -> Add or remove devices and then klick on Add.
Follow the images.
After this you will see on display SCS317 a message Network data received.
In menu Devices, you can see 2 new icons (on the picture below). First icon show Set temperature and second one show Inside temperature. You can set up this device, look on the picture.
On this page, you can name and place device.
Status of device SCS317.
Wake-up the Thermostat - 'Setup > Set up Z-Wave > Send NIF'. If it still shows the 'Waiting for wakeup to configure device' message, go to the device's 'Settings' tab and click 'Configure node right now' and then wake up device again.
If you want change Wakeup interval (s). You can change this option in Advanced option and there set up Wakeup interval (s).
Icon for receiver SSR303 in Fibaro interface.
Note: Check this by turning the temperature on the SCS317 up and down to see that the SSR303 receiver responds accordingly with a green light for ON and a red light for OFF.